aLBI cLAD tf+
ALBI CLAD TF+ 5 gal
WATER BASED THIN-FILM INTUMESCENT FIREPROOFING
Can be used as ASTM E-199/UL 263 Fire Resistant Intumescent Coating or ASTM E-84 Class”A” Fire Retardant Fireproofing.
This hard, durable, abrasion resistant product has a smooth, aesthetic finish. Albi Clad TF is ideal for application in occupied areas or other locations where solvent base fireproofing materials cannot be used. Because of its water-base formulation Albi Clad TF is fully compliant with EPA VOC limits and regulations.
NEXT GENERATION UL CERTIFIED WATER BASED THIN-FILM INTUMESCENT PAINT
Albi Clad TF+ is a water-based, non-toxic intumescent thin film fireproofing material that provides up to 4 hour fire rating on Steel. This hard, durable, abrasion resistant product has a smooth, aesthetic off-white finish. Significantly reduced required Dry Film Thicknesses make TF+ one of the most efficient intumescent products on the market. Albi Clad TF+ is ideal for application in occupied areas or other locations where solvent base or cementitious fireproofing materials cannot be used. Because of its water-base formulation Albi Clad TF is fully compliant with EPA VOC limits and regulations.
•Factory formulated, single component. •UL listed for 1 through 4 hours to ASTM E-119 Standard. • UL Certified Class "A" Fire Retardant Coating tested to ASTM E-84 Standard. •UL tested for resistance to high humidity, heat aging, CO2/SO2 industrial atmosphere and washing. •Attractive off-white finish •Water-based. •Thin film application. •100% Asbestos Free. •Lightweight & hammer-hard. •Will not dust, flake or delaminate• GREENGUARD Certified
PROPERTY TEST METHOD VALUE
Dry Applied Density 85 PCF
Hardness (Shore D) ASTM D2240 67
Cohesive/Adhesion Strength ASTM D4541 485 psi
Abrasion Resistance ASTM D4060 0.111 grams loss (1,000 cycles)
Impact Resistance ASTM D2794 160 inch-lb@2 mm 11.5±
Weight per Gallon 11.5 + 0.20 lbs./gals
% Solids by Volume 70% ± 2.0%
Flame Spread ASTM E 84 5 - Class A
Smoke Developed ASTM E 84 35 - Class A
Albi Clad TF water based Intumescent Coating (Paint) has been tested to ASTM E119/UL 263 and ASTM E84/UL 723 Fire Endurance standards to meet the requirements set forth by IBC/NFPA Building Codes. The product is UL Classified and can be found in UL Product iQ.
You can download Test reports including UL Designs below. Please contact TechMat Supply technical team to receive FREE Consultation on your project.
Albi Clad TF+ intumescent paint (coating) is spray applied directly from the shipping container. Albi Clad TF can be applied to most building materials. All metal surfaces should be primed. Alkyd metal primers are compatible. All surfaces must be clean, dry and free of oil, grease, loose scale, dirt and dust.
Product shall be delivered to the jobsite in factory sealed containers, 5 gallon pails. 55 gallon drums are available by special request.
Spray: up to 45 Mils Wet Film Thickness per Coat
Brush: 10 Mils Wet Film Thickness per Coat
Overcoating is not required with Albi Clad TF+. However, topcoat can be used for color-coding, aesthetics or additional surface protection against spills. For application sites subjected to chemical fumes or spills, the use of a topcoat is recommended. Must be mixed with a drill mixer until product reaches a viscosity to spray.
Airless Sprayer is most effective application method.
Use 1.0 gal. per minute electric airless (minimum) to provide an operating pressure of 3,000 p.s.i. (210 kg/cm2).
** Remove rock catcher from siphon tube.**
Spray tips 0.021"- 0.025". Hose length 50' (15 m) maximum
Product must be mixed thoroughly with mechanical equipment to a
smooth creamy consistency. DO NOT THIN.
Frequent thickness measurements with a wet film gauge are recommended during the application process to ensure uniform thickness.
Final thickness must be measured using an electronic Dry Film Thickness gauge. DeFelsko Positector Gauges from TechMat Supply Co are recommended.
Do not apply Albi Clad TF+ below 50 degrees F. Care must be taken to protect the material from direct rainfall.
Please refer to the Application Manual and Field Guide for further details. Thickness of the application will depend upon the fire endurance rating specified. Installation must be in accordance with manufacturer's printed instructions, and in compliance with specific test requirements.